« PreviousContinue »
4.10.1 General Accessible elevators shall be on an accessible route and shall comply with 4.10 and with the American National Suandard Safety Code for Elevators, DumbwattersEscalators, and moving Walks ANSI A17.1.1978 and 117.18-1979. This standard does not preclude the use of residential a fully enclosed wheelchair lifts when appropriate and approved by administrative authorities Freighi elerators shall not be considered as meeting the requirements of this section, unless the only elevators provided are used as combinalion passenger and freight elerators for the public and employees. 4.10.2 Automatic Operation. Elevator operation shall be automatic. Each car shall be equipped with a sett leveling feature that will automatically bring the car to floor landings within a tolerance of 1/2 in (13 mm) under rated loading to vero loading conditions. This self-leveling feature shall be automatic and independent of the operating device and shall correct the over: travel or undertravel 4.10.3 Hall Call Buttons Call buttons in clevator hobbies and halls shall be centered at 42 in (1065 mm) above the floor. Such call buttons shall have visual signats to indicate when cach call is registered and when each call is answered. Call buttons shall be a minimum of 3/4 in (19 mm) in the smallest dimen. sion. The button designating the up direction shall be on top (see Fig. 20). Buttons shall be raised or nush Objects mounted beneath hall call buttons shall not project into the elevator lobby more than 4 in (100 mm. 4.10.4 Hall Lantema. A visible and audible signal shall be provided of each hoistway entrance to indicate which car is answering a call. Audible signals shall sound once for the up direction and twice for the down direction or shall have verbal annunciators that say "up" or "down.“ Visible signals shall have the following features:
(1) Hall lantern fixtures shall be mounted so that their centerline is at least 72 in (1830 mm) above the lobby floor.
(2) Visual elements shall be at least 2-1/2 in (64 mm) in the smallest dimension
(3) Signals shall be visible from the vicinity of the hell call button tocar lanterns located in can visible from the vicinity of hall call buttons, and conforming to the above requirements, shal be acceptable (see Fig. 20). 4.10.5 Raised Characters on Holstway Entrance All elevator hoistway entrances shall have raised Noor designations provided on both jambs The centerline of the characters shall be 60 in (1525 mm) from the noor. Such characters shall be 2 in (50 mm) high and shall comply with 4.30. Pero manenty applied plates are acceptable if they are permanently fixed to the jambs. (See Fig 20).
4.10.6* Door Protective and Reopening Device. Elevator doors shall open and close automatically. They shall be provided with a reopening device that will stop and reopen a car door and hoistway door automatically if the door becomes obstructed by an object or person. The device shall be capable of com pleting these operations without requiring contact for an obstruction passing through the opening at heights of 5 in and 29 in (125 mm and 735 mm) from the Noor (see Fig. 20). Door reopening devices shall remain effective for at least 20 seconds. After such an interval, doors may dose in accordance with the requirements of ANSI AI7.1.1978 and 117.!1979. 4.10.7* Door and Signal Timing for Hall Calla. The minimum acceptable time from nodication that a ca is answering a call until the doors of that car start to close shall be calculated from the following equation: T- D
or T1.5 Ns
where T - local time in seconds and D - distance (in feet or millimeters) from a point in the lobby or cor. ridor 60 in (1525 mm) directly in front of the farthest